Swimming pool light
I'm an industrial electrician but my next door neighbor called me over 'cause his pool light wasn't working.
1 checked the GFI good
2 removed the light from the pool checked for voltage 12V good.
3 went out and got a new lamp
4 put it back together still did not work
5 removed fixture & lamp checked lamp for continuity good, checked lamp socket for 12V also good.
What am I missing?
Screw in lamp or ?
Poor contacts on the bulb/base ?
But you said you tested contacts....
Pool lamp (12v.) not working?
To what did you check voltage? ground or neutral ? assuming this is a ac low voltage light. If you checked to ground you may still have an open neutral.
Having said that 9 times out of ten in my experience it is a problem with the socket connection with the bulb.
|All times are GMT -5. The time now is 09:13 PM.|
vBulletin Security provided by vBSecurity v2.2.2 (Pro) - vBulletin Mods & Addons Copyright © 2016 DragonByte Technologies Ltd.
User Alert System provided by Advanced User Tagging (Pro) - vBulletin Mods & Addons Copyright © 2016 DragonByte Technologies Ltd.