


Thread Tools  Display Modes 
08262012, 05:26 PM  #1 
Member
Join Date: Jul 2012
Location: Ontario, Canada
Posts: 36
Rewards Points: 25

Split receptacles  reactive loads
A bit of a theory question.
From what I understand, split receptacles are allowed to share a neutral since the two hots come from opposite sides of the panel and are 180 deg out of phase. Therefore, for purely resistive loads, the current in the common neutral should never exceed the wire rating. Question: What about reactive loads? If capacitive and inductive loads are present, it is theoretically possible that the current in the common neutral would exceed the rating of the wire. How does the code deal with this? Advertisement 
08262012, 05:33 PM  #2  
E2 Electrician
Join Date: Apr 2012
Location: Litchfield, CT
Posts: 5,490
Rewards Points: 2,706

Split receptacles  reactive loadsQuote:
Advertisement 

08262012, 05:36 PM  #3 
A "Handy Husband"
Join Date: Feb 2007
Location: South Carolina Low Country
Posts: 4,587
Rewards Points: 2,736

Split receptacles  reactive loads
What type of these loads do you find in a DIY environment?
__________________
Location: Coastal South Carolina 
08262012, 06:09 PM  #4  
Member
Join Date: Jan 2012
Location: IL
Posts: 882
Rewards Points: 760

Split receptacles  reactive loadsQuote:
+pi/2 is the current lead of a capacitor. On the other phase you put an inductive load on it the current will be sin(xpi/2pi), the pi/2 is the lag of an inductor and pi is the alternate phase (180 degrees out of phase). We know sin(x+pi/2) = sin(x3pi/2) therefore the magnitude of the current is exactly 2x the value of either branch. Again the odds of a highly (i.e. near pure inductor) inductive load already are nil in a home, especially one at exactly the branch circuit current rating. Similarly highly capacitive and at the full branch circuit current is also low. The combined probability of these two loads then being on opposite phases of a single split duplex... come on, not going to happen..... 

Thread Tools  
Display Modes  


Similar Threads  
Thread  Thread Starter  Forum  Replies  Last Post 
Split receptacles in kitchen  sanec1  Electrical  30  05132012 02:39 AM 
installing 3 split receptacles  Denisstjean  Electrical  2  05032012 09:10 AM 
Wiring in New Addition?  sandyman720  Electrical  6  11272011 03:34 PM 
Split receptacles, double pole breakers and multiple circuits in a junction box.  morganhammer  Electrical  6  04052011 04:38 PM 
1 switch split receptacles  Price pfister  Electrical  16  05032007 09:01 PM 