Solar Panels 3 Gauge Wire - Electrical - DIY Chatroom Home Improvement Forum

 DIY Chatroom Home Improvement Forum Solar panels 3 gauge wire
 Register Blogs Articles Rewards Search Today's Posts Mark Forums Read

11-09-2011, 02:42 PM   #1
Member

Join Date: Feb 2010
Location: Long Island, NY
Posts: 88
Rewards Points: 75

## Solar panels 3 gauge wire ***Correction 4 GAUGE

Hi, I have a question about my solar panel array. I originally installed a 42 panel array ground mounted about 140 feet from my house were it's connected to the grid. The wire we ran in the ground from the array inverter to the home electrical panel is 3 gauge wire. Now I want to add an additional 12 panel array near the same loaction.

Question: Can I use the existing 3 gauge run, install an electrical panel out by the original 42 panel array and connect breakers from both array inverters to the new electrical panel ? In other words, can I use the same wire or do I need to run a new run to my house ?

Specs:
A) 42 panel array = 7980 watts (currently installed)
inverter max = 7000 watts

B) 12 panel array = 2640 watts inverter max = 2500

THANKS
Attached Thumbnails

Last edited by zman22; 11-09-2011 at 09:42 PM.

11-09-2011, 03:00 PM   #2
Member

Join Date: Feb 2010
Location: Long Island, NY
Posts: 88
Rewards Points: 75

## forgot

Forgot to add that the inverter output is 220

 11-09-2011, 03:13 PM #3 Licensed Electrical Cont.     Join Date: Feb 2004 Location: NY State Posts: 7,821 Rewards Points: 1,992 IMO solar is NOT a DIY type project. Are you a solar or electrical engineer? From the question I have to assume not. What is your background? If my calculations are right, and I doubt they are as I know nothing about solar, I get 10,620 watts. This @ 240v, @ 140' from the house, is around 45 amps @ 240v. The #3cu is WAY overkill even for both sets of panels, even at that 140'.

 11-09-2011, 03:14 PM #4 Member   Join Date: Oct 2011 Posts: 539 Rewards Points: 786 should be ok it is not even 50 amp but i dont think you can connect 2 inverters output in parallel unless specified
 11-09-2011, 03:39 PM #5 Semi-Pro Electro-Geek   Join Date: Jul 2009 Location: Arizona, USA Posts: 3,045 Rewards Points: 2,990 It depends on the inverters. If they are both grid-tie inverters and you're selling power back to the power company, then you should be able to do this with no problem. The inverters will both sync to the grid and deliver their power appropriately. If this is not a grid-interconnected system (i.e. you have a battery bank, inverter/charger combination, or other arrangement) then you probably can't parallel the inverters because they will not synchronize. Definitely read the inverter manuals to see what they say about multi-inverter systems.
 11-09-2011, 05:32 PM #6 Member   Join Date: Feb 2010 Location: MI's Western UP Posts: 600 Rewards Points: 502 3 gauge copper is good for something like 150 amps I believe. 150 amps x 220volts = 33,000 watts. I'd say you can add a few more panels still before you start melting wires
 11-09-2011, 06:12 PM #7 Member   Join Date: Feb 2010 Location: Long Island, NY Posts: 88 Rewards Points: 75 Thanks for all the replies. Yes, both Sunny Boy inverters are grid tie types. Basically I decided to build the 42 panel array 3 years ago when the incentive was at 3.75 per watt but I did not take advantage of the entire 10K watts of rebates. I am not an electrical engineer. Just a very competent guy with electric who has a computer science degree and a couple of electronic technology diplomas. The Town will ultimately approve or not approve the second system the way I want to do it, but I figured there was no better place to ask first than here. BTW: The entire project was definitely a DYI in my opinion. Building a glorified 35 degree deck to mount the panels wasnt too difficult, wiring was simple, and connecting to the grid was a simple procedure of adding a breaker to your panel. Designing it is for the pros. hehe Again thanks for the re-assurance everyone. Oh and, Overkill is my middle name. LOL
11-09-2011, 09:47 PM   #8
Member

Join Date: Feb 2010
Location: Long Island, NY
Posts: 88
Rewards Points: 75

## Correction......

Correction. The run to the house from the inverter is 4 gauge. A friend is telling me that the voltage drop is the main issue. Should this be a concern now with 4 gauge wire and voltage drop calculated in for a 140 foot run ??? This is the hard part to understand. THANKS

Last edited by zman22; 11-09-2011 at 09:50 PM.

 Thread Tools Display Modes Linear Mode

 Posting Rules You may not post new threads You may not post replies You may not post attachments You may not edit your posts BB code is On Smilies are On [IMG] code is On HTML code is OffTrackbacks are Off Pingbacks are Off Refbacks are Off Forum Rules

 Similar Threads Thread Thread Starter Forum Replies Last Post Leo Caproni HVAC 5 10-18-2010 01:23 PM b pahl Green Home Improvement 2 10-07-2009 05:03 PM krisman Electrical 12 01-28-2009 10:34 PM WoodworkerDave Electrical 9 11-17-2008 09:09 PM SURFBUG Appliances 6 10-14-2008 09:41 PM

Top of Page | View New Posts