||11-13-2007 12:08 AM
Smoke detector code?
I would like to know the current code relative to smoke detectors...I believe they have to be hard wired these days, but I was interested in their frquency...Is it one every room now or do they have a sqare footage distance that they must be within...
||11-13-2007 01:13 AM
This is pretty close for all parts of the country. Taken From the US home inspectors website
Where to Place the Detectors
It is important to properly place the smoke detectors in the home. In most locations throughout the U.S., smoke detectors are required in all new homes. The number and location are listed below:
Number and Location Requirements
- The minimum standard as stated in the National Fire Prevention Association's National Fire Alarm Code (NFPA 72): There should be a smoke detector on every level of the house, including the basement and outside every bedroom.
- New homes require hard-wired alarms to be interconnected so that if one alarm is activated, all alarms will sound the alarm signal.
- New homes require smoke detectors in every bedroom.On floors without bedrooms, smoke alarms should be installed in or near living areas, such as family rooms and living rooms.
Additional Guidelines for Installation
- As stated by the NFPA: "Since smoke and deadly gases rise, alarms should be placed on the ceiling at least 4 inches from the nearest wall, or high on a wall, 4-12 inches from the ceiling. This 4-inch minimum is important to keep alarms out of possible "dead air" spaces, because hot air is turbulent and may bounce so much it misses spots near a surface. Installing alarms near a window, door or fireplace is not recommended because drafts could detour smoke away from the unit. In rooms where the ceiling has an extremely high point, such as in vaulted ceilings, mount the alarm at or near the ceiling's highest point."
- If you sleep with your bedroom doors closed, it is recommended that a smoke detector be installed inside each bedroom. Alarms should also be installed in other areas of your home where people sleep.
- Wired systems should not be connected to a circuit that could be turned off with a wall switch.
- Plug-in systems should have a restraining device at the outlet to prevent the plug from accidentally coming loose.
- Hard-wired systems should be installed by a qualified electrician.
- Do not install the smoke detector near windows, doors or forced-air registers where air flow would interfere with the operation of the detector.
|All times are GMT -5. The time now is 11:27 AM.
User Alert System provided by
Advanced User Tagging (Pro) -
vBulletin Mods & Addons Copyright © 2015 DragonByte Technologies Ltd.