i am putting new 14-3 from a new wall box up to a new ceiling fan/light.
2 dimmer switches = 1 fan, 1 light.
wiring them. i think i just connect the black to 1 switch, the red to the other switch. and the white is split to both. is this correct ?
also. cerrowire . when connecting 2 grounds in a box, with or without an outlet. the outlet screw seems to be only large enough for 1 wire. is it ok to just twist the grounds together ? if not, how do i connect them ?