If this is in your service panel the neutrals and grounds can be on eh same buss. If there is a means of disconnect outside between the meter and this panel the neutrals and grounds should be separated. In this case you would have 4 wires coming into the panel.
Answers based on the National Electrical Code. Local amendments may apply. Check with your local building officials.