Got a general question on this.
My home was built in the early 1980s and has a 200A service, GOULD panel.
I've read and been told that
1- There must be a separate ground and neutral
2- then, in following hte above, all the ground connections should be on one side bar
2b. all the Neutral on the other side bar
Did the code changed in this aspect?
My house was done by a licensed electrician and inspected etc.
Is this really all wrong?
OR did the code change?
If the code changed, does this mean now that ANY changes made
have to bring this all up to code?
(in which case, I'm moving :)
If this is in your service panel the neutrals and grounds can be on eh same buss. If there is a means of disconnect outside between the meter and this panel the neutrals and grounds should be separated. In this case you would have 4 wires coming into the panel.
|All times are GMT -5. The time now is 01:31 PM.|
vBulletin Security provided by vBSecurity v2.2.2 (Pro) - vBulletin Mods & Addons Copyright © 2016 DragonByte Technologies Ltd.
User Alert System provided by Advanced User Tagging (Pro) - vBulletin Mods & Addons Copyright © 2016 DragonByte Technologies Ltd.