We recently got a 7000W blackmax generator. I want to install a double throw switch to go between the breaker box main (common), the generator, and the power company line. The breaker box is a crouse-hinds E26095. I found a double throw switch at home depot (http://www.homedepot.com/webapp/wcs/...&Ntpc=1&Ntpr=1).
Would this switch be adequate for the breaker box?
would be acceptable with a neutral kit, assuming incoming service is 100A or less. you would also have to remove the Neutral/ground bond in your main panel, as the double throw switch would become the 'first means' of disconnect.