Running electrical in furred wall
I need to run some pretty basic electrical (a couple of plugs and a couple of switches) through a furred wall.
The existing wall is double wythe brick and I will be furring the lower 2/3rds of the wall using 2x3s on their sides, covered with wainscotting.
I am hoping to be able to use the slim, low profile electrical boxes, and I know that the cable needs to be protected. The house, and all of my work will be in romex, but I know romex cannot be run through conduit.
What do I do here? What type of cable can be run through conduit? Is it "compatible" with romex? Anything special I need to know about tying the conduit cable into the romex?
I think it's ok to run romex inside conduit if it's large enough. See Dave's response in this thread:
If you don't want to use cable, you can run individual THHN/THWN wires (red/white/green) inside conduit. If you go to HD or Lowe's, their individual strands of wire are dual-rated for THHN and THWN. Either of those classifications are fine for dry (indoor) use. May as well just use romex.
3M makes a device called a Stak-it for furring strips to provide for the 1 1/4" standoff distance required for the furring strip.
|All times are GMT -5. The time now is 09:29 PM.|
vBulletin Security provided by vBSecurity v2.2.2 (Pro) - vBulletin Mods & Addons Copyright © 2016 DragonByte Technologies Ltd.
User Alert System provided by Advanced User Tagging (Pro) - vBulletin Mods & Addons Copyright © 2016 DragonByte Technologies Ltd.