||Thread Tools||Display Modes|
|08-12-2014, 01:02 PM||#1|
Join Date: Apr 2008
Posts: 2Rewards Points: 10
Romex in unfinished (studs exposed) basement
I am running romex in two basement rooms. Both have exposed studs. In the one, I am running romex through the joists and across the bottom of the metal cold air return to get to the junction box.
Question#1: Can I run romex across the bottom of that metal cold air return without conduit? if not, what is the best way to transition for that short run?
Question #2: I know i can run romex through the joists in an unfinished basement area... do I have to run conduit from the joist down to the switches or can I just staple the romex to the stud? Not sure what the code is for romex in an unfinished area.
|08-12-2014, 02:08 PM||#2|
Join Date: Nov 2011
Location: Hartfield VA
Posts: 32,738Rewards Points: 10,602
And no one here will ether since there was no location in your profile.
Around here no conduit is required unless it's exposed, other places it all needs to be run in conduit
When posting in forums, letting us know your location will help others give better feedback/advice/solutions to your questions
|The Following User Says Thank You to joecaption For This Useful Post:||
|08-12-2014, 03:57 PM||#3|
Join Date: Sep 2012
Posts: 2,473Rewards Points: 4,288
In a nut shell, it will have to be in conduit if exposed to physical damage.
|08-12-2014, 04:06 PM||#4|
UAW SKILLED TRADES
Join Date: Jan 2007
Posts: 5,341Rewards Points: 2,652
There are areas where the wiring method must be conduit ... Chicago area for an example. The National Electrical code says this .... note that there is no mention requiring protection on a studded wall.. only if you run the romex on the surface of the basement wall. So all this means there is nothing prohibiting you from stapling the romex parallel to the stud as long as you make sure it is 1 1/4" from the face of the stud.
You are also allowed to run romex perpendicular through a cold air return when the cavity between joists is used for that purpose.
C) In Unfinished Basements and Crawl Spaces.
cable is run at angles with joists in unfinished basements
and crawl spaces, it shall be permissible to secure cables
not smaller than two 6 AWG or three 8 AWG conductors
directly to the lower edges of the joists. Smaller cables
shall be run either through bored holes in joists or on running
boards. Nonmetallic-sheathed cable installed on the
wall of an unfinished basement shall be permitted to be
installed in a listed conduit or tubing or shall be protectedin accordance with 300.4. Conduit or tubing shall be provided
provided with a suitable insulating bushing or adapter at the
point the cable enters the raceway. The sheath of the
nonmetallic-sheathed cable shall extend through the conduit
or tubing and into the outlet or device box not less than
6 mm (
1⁄4 in.). The cable shall be secured within 300 mm
(12 in.) of the point where the cable enters the conduit or
tubing. Metal conduit, tubing, and metal outlet boxes shall
be connected to an equipment grounding conductor complyingwith the provisions of 250.86 and 250.148.
" One nice thing about the NEC articles ... you have lots of choices"
|Thread||Thread Starter||Forum||Replies||Last Post|
|Mounting utility faucet on unfinished basement wall connected to pex||dgfit||Plumbing||9||08-25-2013 11:22 AM|
|exposed framing pantry (no drywall) -- romex or MC cable?||amakarevic||Electrical||11||07-10-2013 08:47 PM|
|Want to insulate walls in my unfinished basement||strategery||Insulation||9||08-20-2011 01:35 PM|
|Running a subpanel to unfinished basement||biodieselbob||Electrical||3||08-08-2011 11:44 AM|
|Running Romex up from basement to attic||tra999||Electrical||1||07-25-2006 04:21 AM|