Originally Posted by wrxry77
1 I'm not sure on the breaker so I replaced all of them.
I just wanted to highlight this to stress the importance of a proper panel schedule.
wrxry, it sounds like you have a loose wire somewhere, probably between the breaker and the first outlet. You need to do some homework before anymore troubleshooting.
Start at the panel. Spend an afternoon LABELING IT. Get someone to help you, or use a radio. Start at one end of your house. Plug something in, and start flipping breakers. When that outlet goes dead, write it down (Kitchen counter, left of sink breaker 1 - top left) then go around with a lamp or something portable and check all other outlets to see what else that breaker controls and WRITE IT ALL DOWN.
Once you know what breaker controls this bedroom, start tracing it FROM THE PANEL, look for junction points, etc. CHECK ALL CONNECTIONS. Pull out all the non working receptacles and look for backstabbed connections and change them to using the screws. CHECK ALL CONNECTIONS.