Originally Posted by paul_arc
Yes I put the neutral from the circuit onto the terminal screw for the neut on the breaker and put the neut pigtale from the breaker to the neut bar in the panel
In that case, I bet if you started looking and switch and receptacle boxes, you'd find a ground wire against a neutral terminal somewhere. Could also be a bad breaker. Using a continuity tester, and everything on the circuit in the off position or un-plugged, turn the breaker off and remove the white wire from it. Test for continuity between the free white wire and the ground bar in the panel. If you have a reading, you have a ground and neutral touching somewhere.