Question About Small Voltage Between Neutral And Ground - Electrical - DIY Chatroom Home Improvement Forum

 DIY Chatroom Home Improvement Forum Question about small voltage between neutral and ground
 Register Blogs Articles Rewards Search Today's Posts Mark Forums Read

11-01-2012, 07:26 PM   #1
Member

Join Date: May 2012
Posts: 41
Rewards Points: 55

## Question about small voltage between neutral and ground

Hi,

I have a 15A circuit that powers one outlet and 4 basic light bulb fixtures in my unfinished basement. I just added the 4th light fixture today. The outlet is always powered while the lights are controlled by a switch (which is nothing unusual :-)

I usually sanity check my work before putting covers on lights and outlets by measuring the voltage across the hot and neutral wires and also by doing a quick continuity check with my voltmeter between the neutral and ground wires (by usually, I mean the 3 or 4 times I've done minor wiring projects at home before). Since neutral and ground are at the same potential, I expect to get a steady beep with my meter (i.e. essentially no resistance). When I test this specific circuit, I am getting an intermittent beep rather than the typical continuous one. I measured the voltage across the ground and neutral wires and got a couple of hundred mV. I realize that is not much, but it surprised me as it is higher than what I would expect to see.

With the switch off, I can get the steady beep at the outlet, but as soon as I switch the lights on, the continuity test starts beeping intermittently at that outlet.

I doubt this is a cause for huge concern, but I am confused as to why this is different from what I've seen before.

Any thoughts as to why this is happening? Does anyone else do these types of continuity checks to test the ground and neutral connections?

Thoughts?

11-01-2012, 07:33 PM   #2
Electrical Contractor

Join Date: Sep 2008
Location: Delmarva
Posts: 3,368
Rewards Points: 2,000

You are reading the difference in potential (VOLTAGE) between a current-carrying conductor (NEUTRAL) and a non-current-carrying conductor (GROUND).

All wire has resistance, and while the circuit is in use, you will find that there is a difference between the 2. The more load you have, the greater the voltage difference is.

This is why you must keep them separated beyond the service panel. You don't want any of that return current jumping over to your ground wire, and all the enclosures and other metal parts connected to it.

__________________
-KB

Life is uncertain -- eat dessert first!!

 11-01-2012, 08:08 PM #3 Member   Join Date: May 2012 Posts: 41 Rewards Points: 55 Thanks for your quick response and input - what you're saying makes sense to me so thanks for explaining it. In general, is there a good way to check that a ground wire actually has a proper path to ground? Obviously, I can visually see whether my connections at a specific box are good, but how do I know for sure that everything upstream is also good (e.g. a severed ground wire)? Is it sufficient to do the continuity test I described earlier when there is no load on the circuit, or is there a better way? Thanks!

 11-01-2012, 08:16 PM #4 Electrical Contractor     Join Date: Sep 2008 Location: Delmarva Posts: 3,368 Rewards Points: 2,000 Best way to check is to use a "wiggy" solenoid-type voltage tester. It applies an actual load when testing to ensure a good reading. __________________ -KB Life is uncertain -- eat dessert first!!

 Thread Tools Display Modes Linear Mode

 Posting Rules You may not post new threads You may not post replies You may not post attachments You may not edit your posts BB code is On Smilies are On [IMG] code is On HTML code is OffTrackbacks are Off Pingbacks are Off Refbacks are Off Forum Rules

 Similar Threads Thread Thread Starter Forum Replies Last Post ramatsu Electrical 13 01-10-2012 07:44 PM kgize Electrical 7 04-22-2010 11:40 PM JoulesWinfield Electrical 27 07-26-2009 07:40 PM brotherman Electrical 30 07-15-2008 04:58 PM Silhanek Electrical 4 03-22-2007 06:30 PM

Top of Page | View New Posts