Multiple 120 volt outlets not working is not consistent with a loose neutral?
I always thought 120 volt outlets needed the neutral to work?
No. It's consistent with a loose branch circuit neutral, but not a loose main neutral. A loose main neutral would result in a voltage swing up or down for all 120V circuits in the house, but not complete failure of one circuit. Only a loose main hot or a problem with the branch circuit can cause that.