panel in barn
am looking to have a panel in a barn for power. curious, I have heard that if it is a low number (in this case, 6 slots) that I dont need a dedicated main switch at that location. I have also heard if not real close to master panel/main switch, that it needs a main shut off switch.
Which is it? about 100 feet away from main unit.
A detached building must have no more than 6 switches to turn all the power to the building. So a non main breaker panel with 6 or less breakers meets this code. If you have more than 6 breakers then you need a main breaker or disconnect.
|All times are GMT -5. The time now is 05:55 AM.|
vBulletin Security provided by vBSecurity v2.2.2 (Pro) - vBulletin Mods & Addons Copyright © 2016 DragonByte Technologies Ltd.
User Alert System provided by Advanced User Tagging (Pro) - vBulletin Mods & Addons Copyright © 2016 DragonByte Technologies Ltd.