Originally Posted by longswl
thats what I was looking for. I did not know they made such a box.
Now I have a follow up question....because the cabinets are not in before the electrical inspection, how do I wire this to pass inspection?
I am thinking that I would basically leave the wire rolled up in the area.... one end attached to the switch and the other end rolled up?
Your 1st inspection (rough) just need to show the wire is there ready for cabinet placement. Your final inspection will be after the kitchen is done, where the outlet under the sink will need to be there.
PS - if this is an island free-standing, you do need a 20a gfci protected outlet on the SABC (Small appliance branch circuit) on this island somewhere to satisft the code requirements for receptacles on every counterspace larger than 24".