Outlet quit working
Sounds like a classic backstab failure situation to me. Turn off the breaker that controls this receptacle, the start removing other receptacles that are out looking for a loose neutral. I suspect it will come completely out of the receptacle when you remove it from the box.
Answers based on the National Electric Code. Always check local amendments.