Old house, new light fixture, too many wires
I'm installing a new Ikea chandelier fixture into a bedroom (http://www.ikea.com/webapp/wcs/store...umber=30092475). The old fixture was a simple two bulb fixture. It was controlled successfully by a wall switch.
After taking off the old fixture, I tried to take careful note of two things: the previous wiring arrangement and the other surrounding wires
There are a total of seven wires coming from the ceiling:
-newish black wire
-newish white wire with black electrical tape on it (as a marking?)
-ground wire (bare)
-dingy fabric and insulation covered wire #1
-dingy fabric and insulation covered wire #2
-old white wire
-old black wire
The old fixture was successfully attached to the newish white wire (with electrical tape on it), dingy fabric wire #1, and the bare ground wire.
I needed to buy some new bolts with nuts to attach the Ikea fixture. While at the hardware store, the folks told me to test the other wires. I used a small "test bulb" pigtail (?) tester.
The combination of new white (with black tape) plus fabric wire #1 plus ground does light up the tester--but only dimly. A much stronger test light results from old white wire and old black wire (which were never used in the old fixture).
Here are my questions:
1) Why did the wall switch control the old fixture, but now the test bulb seems unaffected by wall switch?
2) Why does the test bulb appear weak for some pairs, stronger for others?
3) What do fabric-covered wires indicate?
4) Why would there be black electrical tape on a white wire? Did someone try to indicate that it was really acting as the black wire?
5) My Ikea fixture is marked with two wires plus ground. One of the wires is positive, the other neutral. Am I correct assuming positive should go to the white ceiling wire? And that that neutral should go to the black? (n.b. the old fixture was connected white fixture wire to fabric wire #1 and black fixture wire to newish white wire (w/ black tape).
Thanks so much for any insight!
It is common for so many wires to be in the ceiling fixture box. Code requires that all connections be accessible. Placing auxiliary connections in the fixture box avoids having another dummy box with a ceiling or wall plate.
The test light will light bright when connected to one live wire and one neutral/ground wire.
Is there two switches that control this light? Could be it has a three way switch system.
Licensed Philadelphia Electrician
Philadelphia License # 3516 - 16765
If it worked, why did you let these dopes at the hardware store convince you to test ANYTHING?
What you have is PROBABLY an old constant hot light outlet that had a pullchain.
Someone pulled another outlet off that one and then added a switch leg.
If there is a load on the alternate hot out, then you could get all sorts of screwy readings.
I hope you can put it back the way it was.
I had a customer once who put in a "new back door light" "but it doesn't work"
It turned out that he had just installed a new, first-time at this location switch and light fed from the hall light. He didn't think the splices made sense, so he REDID them, along with a few others, at various locations throughout the downstairs of his house [receptacles, switches, lights ...]. It took almost a day to trace the wires and remake the splices so the place would work right.
|All times are GMT -5. The time now is 10:56 AM.|
vBulletin Security provided by vBSecurity v2.2.2 (Pro) - vBulletin Mods & Addons Copyright © 2016 DragonByte Technologies Ltd.
User Alert System provided by Advanced User Tagging (Pro) - vBulletin Mods & Addons Copyright © 2016 DragonByte Technologies Ltd.