good morning to you all.
Sorry for mistake in my writing I'm French from Montreal Quebec.
Woke up middle of the night to go to bathroom
Notice light on the (men this is hard for me had to google to find what
The fan on top of the stove was call :wink:) fan hood was out.
Check the breaker it was on switched it on and of,no luck.
Refergirator is on that circuit:( need milk for my cofee
Back to the kitchen I turn on one of the element on the stove and light on the
Hood and the refregirator were flickering.
Wath is going on.
Verry verry basic knowledge in electricity
I'm in and appartement building 2 unit and a hair salon downstairs
Witch in need to go trough to get acces to the main panel (breaker box is in the appartement)
It's a 100amp with 2 big fuse.
Last year one of the fuse was bad due to bad connection
Did it again a few times ,got fed up went and bought a box
And a 100 amp breaker but the owner never put it up
When ever that fuse use to blow I ended up on one phase
And lights were dim thought out the house witch is not the case
So must be another problem, no idea what it can be.
Will use and extension cord for now to give power to the fridge
It's 4.30 am can't do nothing for now.
Bare with me guys it took me 10 minutes to whrite this.
Just woke up
Weard stuff going on,I notice that everything pluged in outlets
That are out of power would light up and off exactly every 11 second
Like and digital clock would display for 1 second and display again 11 second later.
Never eard of that before.
Time to call the land lord and the power company!
I know but the land lord is off on vacation in Europe
And wouldn't do anything anyway,I bought a box and
100 amp breaker to replace that old box with the 2
Big fuse gave it to him and he never put it on
I still want to find out what's going on,I need that fix ASAP
If I do find out and fix it myself more knowledge
For me :thumbsup:
By the way the dryer has not enough power to turn on
Just and humming sound.
So it could be that one of the fuse blew again ,so I end up on one phase again
Last time it happend all light in the house were dimmed
That is not the case now,I have full power to the rest of the house.
Your landlord legally has to fix it as soon as possible. If the salon is Working fine then its most likely the upstairs service that's messed up. There's many places you can report this to. You need an electrician there as soon as you can get one.
Went to local hardware store bought 2 100 amps fuse
Replace the old one,everything is back on as it should
My next question is how much would it cost me to
Replace the sub panel from the fuse one I have to
Breaker one,that is if everything goes well ,wire not to short ect...
Just to give me a general idea,are we talking 100.00 or more like
At dubo electric a box and breaker goes for around 130.00
Thanks for taking the time to reply.
Well because its a sub panel it may not be too bad. Id say around 1000.
La meilleure réponse est vous devrait faire l'électricien sortir et remplacer le panneau ceci est la façon la plus sûre de ceci faire.
Cependant., vous devriez parler à votre propriétaire d'abord avant que ne vous ceci rapporte autrement ce désordre à l'inspecteur ils diront quelque chose de ce désordre.
Que cela forcera le propriétaire de faire les réparations.
Et votre construction est tant commercal que l'appartement donc il a à faire par l'électricien il n'y a aucune autre voie autour.
The best answer is you should get the electrician to come out and replace the panel this is the safest way to do this.
However., you should talk to your landlord first before you do this otherwise report this mess to the inspector they will say something about this mess.
Which that will force the landlord to do the repairs.
And your building is both commercal and apartment so it have to be done by electrician there is no other way around.
Oh, oui ... Montréal. Si tout cela échoue, descendre à Sainte-Catherine et boire quelques bières.
N'oubliez pas que je suis dans la zone d'Heure de Paris
Vous n'avez pas de vin au déjeuner? Ils le font en Espagne. Je pensais que le vin français a bu toute la journée?
I'm amazed I remember enough French from school that I actually halfways understood that. Well that and the fact we had three t.v channels and one was French as a kid
Of course I will ask an electrician to do it,he has to call
The electrical company so he can cut the seal on the
Thank again guys for reply + you made me :laughing:
Merci pour les conseils les boys.
Tu peut être sur que jva caller une coupe de bierre
Jva aller sur sainte-cat juste pour toé
Pis Avec la temperature qui fait icite y Von's ètre
Bonne en cris + en bonus Avec le soleil ya Dla pitoune
Pas a peut près.
Le vin bon marché n'a pas n'importe quel mieux qu'une bière forte tous les deux le presque même niveau tout cela selon votre goût.
|All times are GMT -5. The time now is 03:05 PM.|
User Alert System provided by Advanced User Tagging (Pro) - vBulletin Mods & Addons Copyright © 2015 DragonByte Technologies Ltd.