neutral / ground bonding ?????
I have a meter base with 200 amp disconnect on a pole then it feeds a 200 amp panel in my house do I need to bond anything in the house panel ??? thanks
Everything should be bonded at the disconnect, and the panel at the house must have a 4 wire feeder.
Local codes may dictate ground rods at the house.
|All times are GMT -5. The time now is 09:19 AM.|
vBulletin Security provided by vBSecurity v2.2.2 (Pro) - vBulletin Mods & Addons Copyright © 2016 DragonByte Technologies Ltd.
User Alert System provided by Advanced User Tagging (Pro) - vBulletin Mods & Addons Copyright © 2016 DragonByte Technologies Ltd.