Need to rewire outlets and lights..HELP
Bathroom light can be on any circuit except special circuits like kitchen counter receptacles. It's the bathroom receptacles that are restricted. The bathroom receptacle circuit must be 20 amp. There are two option for this circuit. Option 1, it can serve anything, including lights and fans, within the bathroom. The circuit can't serve anything outside the bathroom. Option two, If the circuit serve only receptacles it can leave the bathroom and serve receptacles in other bathrooms only.
Holes for cable can be drilled any angle required as long as they stay 1 1/4" from the face of the stud. If they are closer than that then you need a metal protector plate to prevent nails from piercing the cable. When drilling studs best practice it drill in the center.
Do not PM with questions that can be asked in a forum. I will not respond.