So in other words, you are saying that panels that are made to accept taden breakers bring excess neutral bus bars?
I have openned up a few panels here at work, Commercial building where only union electricians are allowed to work in buildings and you should see the inside of these panels. When a circuit is needed, they will just add the circuit and if there is no room in the neutral bus bar, guess what happens, piggy tails inside the panel. This is not just one company we deal with, but several. My concern is my family and don't want something to slap me in the face down in the future. Stubbie worked Great with me trying to figure out this whole thing, and I really appreciate his precious time he took. I was just curious to see if this panel was rated for tandens, since it had a few already. Thanks to all