Originally Posted by dlgobeavs
OK... so I am wiring my house... have done it once before... so I started to get a bit tricky.
I have two circuits for plugs in my kitchen... here was the plan:
Run a 12-3 into the kitchen.
Use the red wire for one circuit... and the black for my second circuit.
I realize that I must run these two circuits off of different "phases" on the panel.
Into my first box I have the following:
12-3 containing both circuits
12-2 leading to the first plug after my black wire GFI
12-2 Leading to a second plug after my black wire GFI
12-2 leading to my red wire GFI
How do I connect the white wires? I can't keep that second one from tripping???
Any advice or diagrams would be MUCHO appreciated.
Hope you can understand my diagram I whipped up.
I assume this is how you have it right?
With multiwire circuits and gfcis, you have to keep the white wire off ANY terminal, must be pigtailed.
You must have a means to disconnect the multiwire circuit completely, a double pole 20 amp should fix this.