- - NEC code
||11-24-2012 05:01 PM
I am wiring a 480 VAC 100 AMP 3 Phase circuit. I am using #3 AWG wires for the power and I would like to know if I can use #4 AWG wire for my ground?
||11-24-2012 06:47 PM
# 8 Cu is sufficient for the equipment grounding conductor on a 100 amp circuit.
|All times are GMT -5. The time now is 11:32 PM.
User Alert System provided by
Advanced User Tagging (Pro) -
vBulletin Mods & Addons Copyright © 2015 DragonByte Technologies Ltd.