Multiple 240V Appliances - Electrical - DIY Chatroom Home Improvement Forum

 DIY Chatroom Home Improvement Forum Multiple 240V appliances
 Register Blogs Articles Rewards Search Today's Posts Mark Forums Read

03-28-2009, 10:02 PM   #1
Newbie

Join Date: Mar 2009
Posts: 2
Rewards Points: 10

## Multiple 240V appliances

I have two cooking appliances that are rated 12A @ 240V in a non-dwelling and not a kitchen (no sink in this room).

Can I put these on a single 30A 2P circuit?

My confusion is that they each use a 15A 240V cord and plug connection. Each is 12A, circuit rating needs to be 12A X 125% = 15A. However, 210.21(B)(3) reads:

(3) Receptacle Ratings. Where connected to a branch circuit supplying two or more receptacles or outlets, receptacle ratings shall conform to the values listed in Table 210.21(B)(3), or where larger than 50 amperes, the receptacle rating shall not be less than the branch-circuit rating.

Tables 210.21(B)(3) and 210.24 identify that receptacles on 30A branch circuits must be rated at 30A. My receptacles will be 15A/240V to match the appliance cords.

Does this mean I have to run two 15A 2P circuits?

03-29-2009, 01:57 AM   #2
Member

Join Date: Feb 2008
Location: Atlanta, Ga/Hamilton, Al
Posts: 2,487
Rewards Points: 2,350

Quote:
 Originally Posted by wirefixer I have two cooking appliances that are rated 12A @ 240V in a non-dwelling and not a kitchen (no sink in this room). Can I put these on a single 30A 2P circuit? My confusion is that they each use a 15A 240V cord and plug connection. Each is 12A, circuit rating needs to be 12A X 125% = 15A. However, 210.21(B)(3) reads: (3) Receptacle Ratings. Where connected to a branch circuit supplying two or more receptacles or outlets, receptacle ratings shall conform to the values listed in Table 210.21(B)(3), or where larger than 50 amperes, the receptacle rating shall not be less than the branch-circuit rating. Tables 210.21(B)(3) and 210.24 identify that receptacles on 30A branch circuits must be rated at 30A. My receptacles will be 15A/240V to match the appliance cords. Does this mean I have to run two 15A 2P circuits?
What are the chances of them being used at the same time? If it's unlikely, you could put them both on a 20 A circuit. Or you could run a 30 A circuit and put a fused switch at each location to protect each one at 15 A. Or you could run a circuit to each one. Which one is the easiest and cheapest and best way to get the job done?

 03-29-2009, 02:00 PM #3 Newbie   Join Date: Mar 2009 Posts: 2 Rewards Points: 10 Both will be used at the same time. I will check the size of the existing conduit to see if I can run separate circuits after derating.

 Thread Tools Display Modes Linear Mode

 Posting Rules You may not post new threads You may not post replies You may not post attachments You may not edit your posts BB code is On Smilies are On [IMG] code is On HTML code is OffTrackbacks are Off Pingbacks are Off Refbacks are Off Forum Rules

 Similar Threads Thread Thread Starter Forum Replies Last Post ruacoltsnut General DIY Discussions 10 11-11-2010 04:05 PM jryali Electrical 19 03-23-2009 11:06 PM poolecw Appliances 2 12-04-2008 02:23 PM home_improver Appliances 2 09-30-2008 06:06 PM

Top of Page | View New Posts