I need to test an element in my hot water heater and I was told to do this I need to:
Here is a diagram of what my meter has:
Can I complete the steps above with this meter? If I use 2000 will that work or will thought make the results different?
Right now when I put it on 2000 and turn it on the screen displays a number 1.
I read on the following link toward the bottom that your element should be about the following...
15.5 ohms for 3500 watts
13.0 ohms for 4500 watts
10.0 ohms for 5500 watts
Let's see... How do I explain this????
If you have a light bulb, there is a wire inside you can see. This wire makes an electrical connection. If the wire is connecting, the light bulb works! Same with a water heater element. It too needs to have the "wire" inside making an electrical connection, then it can heat.
BUT if you have wires connected to the two electrical connections on the element and try to measure "ohms" (or that there is a connection), you could be reading something else connected to the wires like the other element on the water heater.
Therefore it is necessary to disconnect one wire. So disconnect one wire from the element, then read between the two "electrical connection" screws. Do this with your meter set to 200. Then you should get a reading like the above if the element is good. If there is no reading, then the "wire" inside the element is broken and it will not heat.
Another test is to see if there is a "short circuit". This is between one of the electrical connections and a "mounting screw" on the element. This would mean the wire inside the element is "touching" the metal case around it (dangerous/replace). Set your meter to 2000, then you should get the same reading on your meter as when the test probes are not touching anything (no connection).
P.S. The way a water heater works is that first (when water cold) the top element turns on and heats the water in the top of the tank. Then when the water in the top reaches the temperature selected on the thermostat, the upper thermostat turns off the upper element and switches the electricity to the lower element.
Then the lower element kicks on and heats the water in the lower portion of the water heater until the water reaches the temperature selected on the lower thermostat.
Usually the lower element is what runs most of the time unless you use all of the hot water in the tank.
Because of the "switching" needed by the upper thermostat, the upper and lower thermostats are different.
Also warm/hot water comes out from the top of the tank, then there is a "tube" inside the water heater which directs the cold water to go to the bottom of the tank. This is called a "dip tube".
The element resistance (ohms) will be very low, but well above zero. Set your meter first to the 200 ohm scale. Remember the scale is determined by the decimal point. So you can get the same reading on multiple scales, just the decimal point location will be different. But you need to know what the resistance should be first, right?
Use the formula (voltage squared divided by watts). This will give you the resistance reading you want to see. The watts will be listed on the element and the voltage will be determined by the voltage your water heater uses. Usually 240 volts. Measure the voltage with your meter and use this reading. A couple ohms up or down is fine.
I would not test this element with the power on. This is dangerous, and should only be performed by a qualified person.
|All times are GMT -5. The time now is 02:43 PM.|
vBulletin Security provided by vBSecurity v2.2.2 (Pro) - vBulletin Mods & Addons Copyright © 2016 DragonByte Technologies Ltd.
User Alert System provided by Advanced User Tagging (Pro) - vBulletin Mods & Addons Copyright © 2016 DragonByte Technologies Ltd.