Moved ceiling light in bedroom to center, now trips breaker
Yeh I thought your post would be the correct one but when it didn't seem to lead to that....(If breaker is trippin on toggling the switch most likely switched hot is tied to the neutal).... I put up the drawing to help see why that would be the case. In hind sight I should have put up the incorrect wiring diagram. Anyway thanks for the compliments but after all these months together on this forum I just look at all of us as a work crew gettin it done.