Michigan code questions
Adding a stick built addition to an existing mobile and have a couple of questions on the "field correction notice" received regarding the rough electrical inspection.
R109.1.5 (MI residential code?)
Make up wires in electrical boxes.
I can't get hold of the inspector (on vacation) and I don't see that term used anywhere. Any idea what it means?
E3303.3 and NEC 550.32(D)
Branch circuits outside of trailer shall originate at trailer service panel.
550.32(D) doesn't state that and I'm not sure if they are saying that they have to be dedicated circuits (which would be news to me), but again, any ideas?
I appreciate any help. The wiring was completed by a family member (Local 58) and he's done residential before without a hitch. I'm really kind of thrown by the description of the "problems" and was curious if it's common language, or not.
No 1 Means to me that you would have to make all pigtails, and make all ground connections inside any and all boxes before the rough insp.
The way I read 550.32(D) is anything built onto or away from the mobile must not come from the panel inside the home, but from the service disconnect.
Maybe someone else reads it differantly.
|All times are GMT -5. The time now is 04:26 AM.|
User Alert System provided by Advanced User Tagging (Pro) - vBulletin Mods & Addons Copyright © 2016 DragonByte Technologies Ltd.