Main Breaker Tripped?
I recently had a open neutral issue in my breaker box, which caused lights to go bright, and appliances to run fast. I found the loose wire on the neutral bar and tightened it which solved the problem. I also had one of my main breakers to trip before and after this repair, both times have been at night with the dryer running. I have an old GE breaker box my house was built in the late 50's and I don't know when or if any upgrades have been made since the house was built. Would corroted connections on neutral bar cause this? I've had the city out to check thier end and they claim it's good.
Thanks in advance!