I just bought a condo at auction and the bank sent someone in to clean it up and (4) 3" can lights were installed,they ran the main lead into the closet into some type of box.(some type of transformer?)on one side the black,white and ground go in on the back side it has were like a plug would go in. The box is marked lightspeed MDL# DA105 12P. I can't find it anywhere.
My question is can I take that out and just run line to switch and bypass box?
Thanks in advance
Last edited by zombie911; 09-09-2008 at 12:10 PM.
Thats what I thought... I guess I could run a hot to the transformer, but I would like to find the pigtail that plugs into the box, anyone have any idea where to find this company it does not pull up anywhere on the web..