light switches wired in series -- why?
the only thing wrong with the setup might be if switches 2 and 3 have 2 wires under 1 screw. That's not allowed.
The other option for this would be to pigtail the incoming hot with 4 leads off it (1 to each switch)
The way a setup like this works is there is 1 incoming cable (hot, neutral and ground) coming into the switchbox to power ALL lights and the receptacle that is switched) instead of running power to them and having a switch loop.
I DON'T OWN MY HOUSE...
MY HOUSE OWNS ME!
Last edited by CowboyAndy; 05-11-2008 at 12:19 PM.