Kitchen Lighting Circuit
I have an entry landing that I want to hang a light in. Can this be taken from the kitchen lighting circuit, per 2008 code?
The kitchen is right off the entry.
Yes it can be taken off the circuit that is feeding the kitchen lights, just not any 20a circuit that is feeding any of your countertop receptacles, appliances, dining room receptacles, or bath gfi receptacle.
|All times are GMT -5. The time now is 12:13 AM.|
vBulletin Security provided by vBSecurity v2.2.2 (Pro) - vBulletin Mods & Addons Copyright © 2016 DragonByte Technologies Ltd.
User Alert System provided by Advanced User Tagging (Pro) - vBulletin Mods & Addons Copyright © 2016 DragonByte Technologies Ltd.