The box has two seperated busbars for the hots, neutral bar on the top right and I'll put a grd bar in. I just need 120V on each side not 240V total because I need the two circuits separated for the two 15A breakers with 14Awg out of them. Would two 14awg hots be fine to supply this SP, 20 feet from the panel in the basement, washer located in the same place and the pool is less then 150 feet (of wire) away.
Q2: off this subject, is 10awg good for 40A if the run is less then 30 feet?
old work.....seems like this house was made from scrap parts!