||Thread Tools||Display Modes|
|10-08-2012, 04:22 AM||#1|
Join Date: Sep 2012
Posts: 53Rewards Points: 49
how to upgrade an older home electrical
I want to upgrade a fusebox panel and probably the conduits.
ITs an older single story small home with 2 br and a bath.
All the conduits are running in the attic ontop of the rafters.
If i get a new "service" is it ok to run the conduit above
the rafters instead of thru the rafters?
If the receptacles are really loose in the cinderblocks should
I think about getting a whole new "electrical service" done?
|10-08-2012, 04:42 AM||#2|
Join Date: Sep 2009
Location: Kane county,Illinois
Posts: 25,728Rewards Points: 7,174
New wires are usually pulled through the existing conduit----even when old the conduit is seldom replaced.
Is there a reason you wish to do that?
New boxes can be added to the existing conduit if the old boxes aren't suitable for todays needs.
I'm not an electrician--one will be along soon,
Where are you? Most places in Canada and the US allow Romex in residential construction---so wiring could also be added using that instead of conduit.
New members: Adding your location to your profile helps in many ways.--M--
|10-08-2012, 05:57 AM||#3|
Join Date: Nov 2011
Location: Oviedo, FL near Orlando
Posts: 227Rewards Points: 150
Ditto, what oh'mike said. FYI, "electrical service" usually refers to some combination of, the weatherhead, meter can, and, first and/or largest panel. Get detailed estimates to know how each electrician defines that term. Replacing all the rest of the wiring is a whole house rewire.
A whole house rewire is probably unnecessary. Additional circuits may be advisable. Existing conduit is safe above the rafters and grandfathered in.
Conduit resists physical damage much better than romex, and it lasts forever, except for rust. To rust out conduit requires chronic and severe water damage, seldom found in attics. Loose conduit joints can compromise your ground. And if you have wobbly boxes, you may have hidden, loose joints. The easy fix is to include a bare wire with any replacement pull.
Rafters are load bearing. There are building codes that specify the size and location of holes. For safety, know before you drill.
Expansive hydraulic cement might be the answer to loose boxes in cinder block. It expands to wedge the boxes in tight. Regular cement shrinks. Fill a plastic bag and cut off a small piece of the corner. Use it like a pastry chef. Fill between box and block.
Last edited by Glennsparky; 10-08-2012 at 06:46 AM.
|Thread||Thread Starter||Forum||Replies||Last Post|
|fireplace dimensions on older home...can it burn wood?||JPinSD||General DIY Discussions||6||12-18-2010 08:40 AM|
|Rewiring older home||Rt2frdm||Off Topic||4||08-23-2010 11:35 AM|
|OLDER HOME, 100 amp box etc..||BADAZZVOLKS||Electrical||2||10-29-2008 02:36 PM|
|Please Help - Weird electrical issue affecting home network||sxpsxpsxp||Electrical||23||02-03-2008 11:42 AM|
|Polarized plug light fixture- Hardwire to home electrical?||timdavis3824||Electrical||3||07-09-2007 12:34 PM|