How Much Current Draw - Electrical - DIY Chatroom Home Improvement Forum

 DIY Chatroom Home Improvement Forum How much current draw
 Register Blogs Articles Rewards Search Today's Posts Mark Forums Read

12-10-2006, 08:41 PM   #1
Member

Join Date: Apr 2006
Location: St. Louis, MO
Posts: 46
Rewards Points: 25

## How much current draw

I understand I can run 20amps on a 12 guage wire but I have a cable that is 12/3, ie, red, white, black, green. So my question is, can I run 20amp on both the red and black?

I'm confused because I would think the return white wire would still only be rated for 20amps total but if the other two ran 20 then that would put a 40amp load on the white wire.

What am I misunderstanding?

12-10-2006, 09:07 PM   #2

Join Date: Feb 2004
Location: NY State
Posts: 7,821
Rewards Points: 1,992

Copied from my reply on the other forum:

Quote:
 It is actually the opposite. The white will only carry the imbalance of the two circuits of a multi-wire circuit. For instance, if the black is carrying 10 amps, and the red is carrying 7 amps, the white is only carrying 3 amps. Understand? This is provided the multi-wire circuit is wired correctly. Meaning the two hots are on different "phases" in the panel.

__________________
Sometimes I feel like if I answer any more questions it is like someone trying to climb over a fence to jump off a bridge and me giving them a boost.

 12-16-2006, 02:36 PM #3 Member   Join Date: Apr 2006 Posts: 90 Rewards Points: 79 Speedy Petey is right about having the "hot" wires on 2 different phases in the panel. To check this, you should have 240 volts (or close to it) from black to red. If you have nothing from black to red, then both "hots" are from the same phase...and you would be overloading the neutral (white) wire, as you first mentioned. "Edison 3-Wire Circuit"...http://www.bobvila.com/BBS/3_wire-El...l-1-T1593.html

 Thread Tools Display Modes Linear Mode

 Posting Rules You may not post new threads You may not post replies You may not post attachments You may not edit your posts BB code is On Smilies are On [IMG] code is On HTML code is OffTrackbacks are Off Pingbacks are Off Refbacks are Off Forum Rules

 Similar Threads Thread Thread Starter Forum Replies Last Post JoulesWinfield Electrical 27 07-26-2009 07:40 PM Fat b Remodeling 4 05-04-2007 07:09 PM aperionguru Electrical 1 03-14-2007 04:42 AM kahuna44 Electrical 8 03-02-2007 10:25 AM allenroad Electrical 1 03-19-2005 07:24 PM

Top of Page | View New Posts