A HO Asks You - Electrical - DIY Chatroom Home Improvement Forum

 DIY Chatroom Home Improvement Forum A HO asks you
 Register Blogs Articles Rewards Search Today's Posts Mark Forums Read

07-24-2012, 02:54 PM   #1
Member

Join Date: Jul 2008
Location: NW of D.C.
Posts: 5,990
Rewards Points: 2,000

if he or she is getting the full power delivery capability of his/her 200A residential service so you rent a 48 kw jobsite heater and head over.

With no load on the panel you read 240.0 v and with the heater on you read 216.0 v.

In answer to the HO's question, what say you?

07-24-2012, 03:08 PM   #2
Member

Join Date: Dec 2011
Location: New york
Posts: 1,053
Rewards Points: 500

What is the question?

__________________
Electricity will kill you if you give it a chance

 07-24-2012, 03:18 PM #3 Member   Join Date: Jun 2012 Location: Phoenix AZ Posts: 452 Rewards Points: 250 What say I is... Where did you plug the 48KW heater in at?

 07-24-2012, 05:17 PM #4 Member   Join Date: Aug 2011 Location: Louisville, KY Posts: 266 Rewards Points: 349 I'm not an electrician, but I like puzzles, so here is my take. If it's a 48kW, 240V heater, it's designed to pull 48000/240=200 A, so it's resistance is 240/200=1.2 ohms. Since there is only 216 V through it, it means it only pulls 216/1.2=180 A. At these currents and resistances, wire resistance is not negligible. So in fact we have a circuit with a 1.2 ohm machine and some wire with resistance R connected in line. We know (assume) that voltage is 240 V at the transformer, so we have that total resistance of the circuit is 240/180=1.333 ohms. That means that total wire (plus connections, etc) resistance is 0.133 ohm. Plausible to me. So I would say, it's normal. That said, I'm also wondering where he/she plugged it in, given the fact that it's pulling 180A. Operating that beast costs \$5/hr, wow.
07-24-2012, 06:48 PM   #5
Member

Join Date: Jul 2008
Location: NW of D.C.
Posts: 5,990
Rewards Points: 2,000

Quote:
 Originally Posted by Julius793 What is the question?
...if he or she is getting the full power delivery capability of his/her 200A residential service

07-24-2012, 07:18 PM   #6

Join Date: Feb 2004
Location: NY State
Posts: 7,757
Rewards Points: 1,864

Quote:
 Originally Posted by Yoyizit ...if he or she is getting the full power delivery capability of his/her 200A residential service
If you think I am going to go out and rent a 48kW heater and hook it up to the main service you're NUTS!

Where the hell do you rent a 48kW electric heater anyway???
__________________
Sometimes I feel like if I answer any more questions it is like someone trying to climb over a fence to jump off a bridge and me giving them a boost.

 07-24-2012, 07:21 PM #7 Member   Join Date: Feb 2010 Location: Oklahoma Posts: 992 Rewards Points: 506 Is the 48kw heater assumed to be accurately spec'd and labeled?
 07-24-2012, 07:25 PM #8 E2 Electrician     Join Date: Apr 2012 Location: Litchfield, CT Posts: 5,655 Rewards Points: 2,970 What would be the point of this? __________________ House in Progress Bar I built...
07-24-2012, 07:27 PM   #9
Member

Join Date: Feb 2010
Location: Oklahoma
Posts: 992
Rewards Points: 506

Quote:
 Originally Posted by stickboy1375 What would be the point of this?
To melt a transformer?

 07-24-2012, 07:29 PM #10 Electrical Contractor     Join Date: Sep 2008 Location: Delmarva Posts: 3,368 Rewards Points: 2,000 MOST power company transformers are undersized. It is quite common to have several houses connected to the same 25 or 50 kVA transformer. It's also common to have an overhead wire that appears to be undersized, such as a #4 aluminum ACSR serving a 200 Amp service. 25kVA is just over 100 Amps, and is usually just fine to serve a couple of houses with 200 amp services. They can operate at twice the rated capacity for a short duration if necessary. Power companies apply demand factors to their design of the grid to keep infrastructure costs to a reasonable level. The problem is when you max out a residential panel by switching on a 48 kW load, you can discover the limits of a transformer, the connectors, wires, etc. If one wanted to permanently connect such a load, the POCO would certainly need to upgrade some of their local grid to handle the load(s), and possibly pass on some of the costs to those who require the unusually heavy loads. Some folks who install electric on-demand water heaters find out this the hard way.... __________________ -KB Life is uncertain -- eat dessert first!!
 07-24-2012, 07:32 PM #11 Semi-Pro Electro-Geek   Join Date: Jul 2009 Location: Arizona, USA Posts: 2,996 Rewards Points: 2,892 I say no. 10% voltage drop is unacceptable.
 07-25-2012, 10:08 AM #12 Member   Join Date: Jul 2008 Location: NW of D.C. Posts: 5,990 Rewards Points: 2,000 Thanks especially to KBSparky and Mpoulton for understanding the letter and the spirit of my question and answering it. http://www.google.com/search?client=...w=1093&bih=741
07-25-2012, 06:02 PM   #13

Join Date: Feb 2004
Location: NY State
Posts: 7,757
Rewards Points: 1,864

Quote:
 Originally Posted by Yoyizit Thanks especially to KBSparky and Mpoulton for understanding the letter and the spirit of my question and answering it. http://www.google.com/search?client=...w=1093&bih=741
You're welcome.
__________________
Sometimes I feel like if I answer any more questions it is like someone trying to climb over a fence to jump off a bridge and me giving them a boost.

 The Following User Says Thank You to Speedy Petey For This Useful Post: Julius793 (07-25-2012)
 07-26-2012, 12:50 PM #14 Member   Join Date: Aug 2011 Location: Louisville, KY Posts: 266 Rewards Points: 349 I'm happy that everyone is satisfied, but my curiosity won't let me rest. So do you guys say that 0.13 ohm resistance for the circuit is impossibly high? Or something was wrong with my calculations? Just to clarify basically what I said was the following: every time you operate an electronic device, you connect the device in series with the wires. Everything in a series circuit gets a voltage that is proportional to its resistance. If the wires have 0.13 ohm resistance, that is usually negligible, because almost everything has much higher resistance in the circuit, like a 60 W bulb has 120 ohms resistance. But this monster heater has only 1.2 ohms resistance, so the wires are not negligible, so they eat up some of the voltage (and heat up in the process). So either I messed up something or you say the circuit can't have 0.13 ohm resistance.
07-26-2012, 01:41 PM   #15
Semi-Pro Electro-Geek

Join Date: Jul 2009
Location: Arizona, USA
Posts: 2,996
Rewards Points: 2,892

Quote:
 Originally Posted by csab_ I'm happy that everyone is satisfied, but my curiosity won't let me rest. So do you guys say that 0.13 ohm resistance for the circuit is impossibly high? Or something was wrong with my calculations? {snip} So either I messed up something or you say the circuit can't have 0.13 ohm resistance.
0.13 ohm resistance for the service (which is what's being measured, not the branch circuit's resistance) is too high. 10% voltage drop is unacceptable. If it's a REAL 200A service that can actually be used for 200A total load, then it would have to have low enough voltage drop at full load to stay within reasonable voltage specifications. That's typically 5% or less, but 3% would be better.

 The Following User Says Thank You to mpoulton For This Useful Post: csab_ (07-26-2012)

 Thread Tools Display Modes Linear Mode

 Posting Rules You may not post new threads You may not post replies You may not post attachments You may not edit your posts BB code is On Smilies are On [IMG] code is On HTML code is OffTrackbacks are Off Pingbacks are Off Refbacks are Off Forum Rules

 Similar Threads Thread Thread Starter Forum Replies Last Post noone Carpentry 4 11-21-2011 05:39 AM WGFA Plumbing 8 10-08-2011 11:16 AM HVACMac HVAC 2 08-13-2011 01:20 PM

Top of Page | View New Posts