Help with bathroom wiring - URGENTLY NEEDED
Not to be a jerk but if you can't figure out how to wire 3 switches from one source, why are you even doing electrical work. Guess i should be thankful i am not your neighbour.
I am also a nice guy so i will tell you how to do it. I assume all your switches are in the same box. There are two ways to do it, you can take the one wire coming in and make 3 pigtails with it. Take 3 pieces of wire about 6" long, make a joint with the source and then you have 3 wires for your switches.
You can also leave the source wire really long and at the first switch take enough insulation off the wire to go around the screw(don't cut it yet) continune onto the second switch, strip enough insualation to go around screw(put those side cutters away, not time to cut yet) go to the last switch cut it off put a loop and attach it the screw, then you have power at all 3 switches. Hope that makes sense for you.