||Thread Tools||Display Modes|
|11-21-2012, 03:05 PM||#1|
Join Date: Nov 2011
Posts: 75Rewards Points: 91
hard wire fan vs plug
I bought a new vent hood for my stove. (Broan PM390) My electrian already ran a hard wire (120V) to where the fan will go above the stove. The fan comes with a power cord to plug into a 120V outlet. It will be a pain for me to now install another outlet up in that area to plug this into- Can I just wire this unit direct into the 120V line I already have run? I would insure it's connected properly with connections in box etc.....
|11-23-2012, 12:08 AM||#2|
Join Date: Nov 2012
Posts: 350Rewards Points: 250
hard wire fan vs plug
Below is from the Broan installation guide.
It says to use the supplied cord and plug.
The only code issue I can think of is that it might only meet it's UL listing with the supplied cord and plug.
If you want to be certain that hard wiring will not void the UL listing, you should call Broan and ask them.
Note: This range hood must be properly grounded. ALWAYS SWITCH OFF THE ELECTRICITY SUPPLY BEFORE
CARRYING OUT ANY OPERATIONS ON THE APPLIANCE.
The unit should be installed by a qualified electrician in accor-
dance with all applicable national and local electrical codes.
This appliance must be grounded. In the event of an electrical short
circuit, grounding reduces the risk of electric shock by providing an
escape wire for the electric current. This appliance is equipped
with a cord having a grounding wire with a grounding plug. The
plug must be plugged into an outlet that is properly installed and
WARNING - Improper grounding can result in a risk of electric shock.
Consult a qualified electrician if the grounding instructions are not
completely understood, or if doubt exists as to whether the appliance
is properly grounded.
Do not use an extension cord. If the power supply cord is too short,
have a qualified electrician install an outlet near the appliance.
Position the electrical outlet at a maximum distance of 33-7/16” (85
cm) from where the lead exits from the hood (see illustration along-
Fit the plug into the outlet.
|Thread||Thread Starter||Forum||Replies||Last Post|
|my Firex hard wire smoke alarms have no grounding||amakarevic||Electrical||11||01-14-2012 09:25 AM|
|Wire hardwired fixture to plug||seansy59||Electrical||11||08-03-2011 10:42 AM|
|HALP! Master/Remote Dimmer troubles!||Confuserated||Electrical||9||02-12-2010 04:30 PM|
|Running new dryer wire...but dryer is three plug currently.||RyanD||Electrical||7||08-07-2009 03:33 PM|
|Neutral Wire?||4x15mph||Electrical||8||11-24-2008 02:00 PM|