Register Blogs Articles Rewards Search Today's Posts Mark Forums Read

11-12-2011, 07:13 PM   #1
Newbie

Join Date: Nov 2011
Posts: 5
Rewards Points: 10

I have a 220 circuit running from my barn to my well house. The meter is at the barn and the feeders connect in the box containing the meter. There are three wires connecting the well house, all three black with one having a white stripe. I assume the one with the white stripe is the neutral. The wires run underground until they reach the well house and then one is yellow inside. After testing with a meter the yellow is the neutral the two black each have 120v.

My well pump is 220 and works fine with or without the yellow wire connected to the breaker box.

If I connect a single 30 amp breaker to the braker box that connects to one phase of the circuit (120v) and put a load on the circuit, it drops all voltage.

I assume there is a problem with the main yellow (and then black with white stripe) wire that goes back to the meter.

Any ideas or suggestions? Also, how can the 220 work without the neutral to complete the circuit?

Thanks.

11-12-2011, 07:39 PM   #2
I=E/R

Join Date: May 2010
Location: Minnesota
Posts: 2,052
Rewards Points: 1,000

You need to do some more research. Are you telling us that the feeder to the pump comes straight off the meter lugs? If so that makes them unfused service conductors. Does the pump house have any type of electrical panel?

11-12-2011, 08:10 PM   #3
Member

Join Date: Nov 2009
Location: Albany, GA
Posts: 295
Rewards Points: 250

Quote:
 Originally Posted by ajleeburton how can the 220 work without the neutral to complete the circuit? Thanks.

The neutral balances the potential voltage between the two legs. If you measure voltage across the two hots, you should see about 240V. Measuring between either hot and the neutral should result in 120V.

You need to describe your setup in a little more detail. You mentioned a breaker box... does your service from the meter connect to a breaker box, and the pump is connected to breaker in that box?

Also, what exactly are you trying to accomplish with a 30A 120V circuit? That's a bit hefty for a 120V circuit (although not entirely out of the question).

11-12-2011, 09:40 PM   #4
Newbie

Join Date: Nov 2011
Posts: 5
Rewards Points: 10

I put a 30 amp breaker in because I tripped the 20 amp with the heat lamp I put in the well house last winter to thaw the pipes. I will put a permanent heat lamp in there this winter with a thermostat to automatically turn on at about 38 degrees.

The well pump really doesn't come into play with the problem. I removed the 50 amp breaker for the pump completely from the breaker box and still had the same problem. The only thing I had on the breaker box was the 120v breaker and the voltage still went to zero with a load.

I see ~250v across the two legs combined and 120v each so I know both are working fine.

Yes, the service from the meter connects to the new breaker box I put in about a year and a half ago. Everything worked fine until I plugged in the heat lamp and tripped the breaker (or whatever damage it did). I have also replaced the 120v breaker with a new breaker with the same result.

Logically, the only thing left that hasn't been replaced is the Neutral wire that connects the breaker box to the service from the meter.

Thanks,
Lee

11-12-2011, 09:45 PM   #5
Newbie

Join Date: Nov 2011
Posts: 5
Rewards Points: 10

## corsair

The service comes from the meter and feeds into a new breaker box in the well house. One black wire feeds the top bus and the other black wire feeds the bottom bus. The yellow wire is connected to the grouding strip on top.

The pump has it's own electrical box that feeds from the breaker and then goes to the pump.

However, even if I take the entire pump loop out of the process, I have the same problem with the outlet losing voltage. I removed the pump breaker from the breaker box.

Thanks,
Lee

 11-12-2011, 09:53 PM #6 Newbie   Join Date: Nov 2011 Posts: 5 Rewards Points: 10 Also, I consulted a local home improvement store and spoke with the resident "expert". He suggested a ground wire connected to a grounding rod driven in the ground. I ran a number 8 copper wire outside the well house and drove a steel rod 5 feet in the ground and connected the two. I connected the copper wire to the grounding strip on the top of the breaker box. I got the same results.
11-12-2011, 10:14 PM   #7

Join Date: Sep 2007
Location: Maryland
Posts: 10,820
Rewards Points: 1,794

Quote:
 Originally Posted by ajleeburton Also, I consulted a local home improvement store and spoke with the resident "expert". He suggested a ground wire connected to a grounding rod driven in the ground. I ran a number 8 copper wire outside the well house and drove a steel rod 5 feet in the ground and connected the two. I connected the copper wire to the grounding strip on the top of the breaker box. I got the same results.
Grounding rods have no part in the proper operation of the circuit under normal conditions. The "expert" gave you bum scoop.
__________________
Answers based on the National Electrical Code. Local amendments may apply. Check with your local building officials.

 The Following User Says Thank You to Jim Port For This Useful Post: mpoulton (11-13-2011)
 11-12-2011, 11:53 PM #8 Member   Join Date: Nov 2011 Location: Prather California Posts: 40 Rewards Points: 25 You could have a break in the line. It will show voltage with a meter but fail under load. Had that problem last year with one leg to my house panel. Power company came out and found the break
11-13-2011, 10:41 AM   #9
I=E/R

Join Date: May 2010
Location: Minnesota
Posts: 2,052
Rewards Points: 1,000

Quote:
 Originally Posted by ajleeburton Also, how can the 220 work without the neutral to complete the circuit? Thanks.
A 220 (240) volt circuit doesn't use a neutral. It is starting to sound like the wiring to the pump house isn't done correctly. From your description of the underground wires, black with white stripe, is appears that you have USE feeding your pump house. Maybe that white striped wire isn't connected to the neutral bar at the meter. Without pictures we won't get far with this.

11-13-2011, 02:15 PM   #10
Newbie

Join Date: Nov 2011
Posts: 5
Rewards Points: 10

Thanks everyone. I will have the electric company check the neutral wire for a break.

FYI, I buried a new wire this morning from another breaker box in my barn (that breaker box is on a separate feed) to my well house. I used the new 120v breaker in the breaker box in the barn and all is working flawlessly.

Thanks again for all of your responses.

 Thread Tools Display Modes Linear Mode

 Posting Rules You may not post new threads You may not post replies You may not post attachments You may not edit your posts BB code is On Smilies are On [IMG] code is On HTML code is OffTrackbacks are Off Pingbacks are Off Refbacks are Off Forum Rules

 Similar Threads Thread Thread Starter Forum Replies Last Post mstanleyg Building & Construction 10 03-30-2010 12:38 PM n0c7 Electrical 10 10-06-2008 03:20 PM CaptHanky Electrical 45 06-27-2008 09:18 AM Matth3w General DIY Discussions 5 06-11-2008 06:26 PM Mike McBride Building & Construction 2 01-09-2007 01:51 PM

Top of Page | View New Posts