I am running a new 20 amp circuit to my outdoor screened porch and deck. Local code requires all receptacles to be gfci. I want to run 5 receptacles in line and independent of each other. In other words, I don't want one receptacle to trip the others. help, please.
...but do remember that if you overload one receptacle (or have a short)...you will still lose power to all of them when the breaker trips in the panel. Having separate GFCIs will indeed prevent a GFCI trip from affecting the other receptacles.