||12-13-2010 11:47 AM
I recently removed wiring in conduit that hung on the bottom of the joist in my basement so I could feed the circuits that were fed with romex stapled inbetween the joists. After completing I noticed that the light on my GFCI were on in the circuits that were fed. The recepticles still work but the test button is stuck in and the reset button doesn't do anything. I bought a GFCI tester to see if it was wired wrong but it says that everything is ok. I checked the connections in the junction boxes in the basement and made sure they were all ok. I am basically at a loss and don't know what else to do other than see if replacing the GFCI outlets help. There are two seperate circuits that both have the same issue so I have a hard time believing it is a bad outlet. Any help is much appreciated!