I'm working on an electrical plan for our upcoming house we're going to build. I'm looking for some opinions and feedback on the electrical plans I've made up. Have a look and let me know what you think.
The first circuit I counted in the garage had 13 outlets. You are limited to max 12 outlets per circuit in Canada.
I don't think I see a receptacle on the front porch. You need at least one receptacle on all outdoor balcony, porches and decks.
Do not PM with questions that can be asked in a forum. I will not respond.
The Following User Says Thank You to joed For This Useful Post: