Originally Posted by LawnGuyLandSparky
Doesn't seem to me your alternative is much of an improvement...
Beauty is in the eye of the beholder
IMO, a 6x6 box is much less of an eyesore than a old full length dead breaker box. If it was as simple as boarding it over I would.
Originally Posted by CowboyAndy
Why is there a green wire spliced with a group of reds? If that is a hot wire, then you should mark it somehow to note that it is hot. USe something like a sharpie and color ot black or red, or use black or red tape.
I'm a novice, but understand. I'll mark it accordingly.
After pulling the covers off, I see there is a large white wire connecting to the bar with the ground. I believe it's called a neutral bus bar.? Can you advise how to deal with this? Thanks.