- - eletrical
||06-17-2005 02:15 AM
If you have a 200 AMP electrical service panel, can you run a 100 amp into it or does it have to be 200 amp into it
||06-17-2005 06:18 AM
Does it have a main breaker? If it is a main lug panel rated at 200 amps, you can run any size up 200 amps. If it has a main breaker, then you must feed it with 200 amps.
|All times are GMT -5. The time now is 01:22 PM.
User Alert System provided by
Advanced User Tagging (Pro) -
vBulletin Mods & Addons Copyright © 2015 DragonByte Technologies Ltd.