I needed to replace some old switches for the disposal and the "over the sink" light that were from the 70's. They were configured differently than the new switches that I purchased. I also noticed that the old switches were not grounded. I ended up pulling it all out and hope to do it correctly. Previously all the white wire was conected together welded and taped, then the hot black was run with a section cut out of the center that was then strung to the next switch. I don't think that was correct either. Any help doing this correct is greatly appreciated.
Last edited by ColdYeti; 07-06-2012 at 02:05 PM.
Reason: Added text.
Do It like it was before. It was fine.
Connect all the whites together with a wire nut.
Connect all the grounds together and to the switches.
Connect the power black to two short black pigtails with a wire nut.
Connect one pigtail to each new switch.
Connect the black from the light and GD to the switches.
The Following User Says Thank You to joed For This Useful Post: