Electrical Panel - Electrical - DIY Chatroom Home Improvement Forum

 DIY Chatroom Home Improvement Forum Electrical panel
 Register Blogs Articles Rewards Search Today's Posts Mark Forums Read

07-05-2013, 02:12 AM   #1
Newbie

Join Date: Jul 2013
Posts: 9
Rewards Points: 10

## Electrical panel

I added a sub panel in my garage. I found that on the main pane,l the bus bar to the box is energized @ 120 v. The neutral bar to the box has no current. Any thought on why I'm getting power between the bus bar and the box or how to best trouble shoot?

thanks
Bill

07-05-2013, 06:37 AM   #2
Electrical Contractor

Join Date: Apr 2008
Location: Chester, VA.
Posts: 1,054
Rewards Points: 510

Do you mean the buss where the breakers stab into?
If so, it's because the box is bonded to the neutral (grounded conductor) in the main box.

This way, if the box comes in contact with an ungrounded conductor, it'll trip the breaker.

Therefore, no problemo

07-05-2013, 11:38 AM   #3
Newbie

Join Date: Jul 2013
Posts: 9
Rewards Points: 10

## Thanks

I had that sneaky suspicion after researching it last night. I wasn't 100% certain and was worried something was wired incorrectly or I had a chaffed wire. Thanks for your input, I'm feeling much more comfortable.

 07-05-2013, 01:40 PM #4 Civil Engineer   Join Date: Mar 2009 Location: Boston Posts: 5,493 Rewards Points: 4,566 Are you sure the neutral has no current? I am guessing you mean that you measured the voltage on the neutral and measured zero volts. Under load, the neutral is going to carry the difference in current between the two 120V legs in your panel. Since the legs are rarely exactly in balance, under virtually all circumstances you should measure current on the neutral, although voltage should be close to 0 (the neutral is at ground potential, which by ordinary definition is assumed to be 0 volts).
 07-07-2013, 05:22 PM #5 Newbie   Join Date: Jul 2013 Posts: 9 Rewards Points: 10 Yes Daniel, you are correct in your assumption. When measuring voltage from neutral to the panel, I was getting 0.

 Thread Tools Display Modes Linear Mode

 Posting Rules You may not post new threads You may not post replies You may not post attachments You may not edit your posts BB code is On Smilies are On [IMG] code is On HTML code is OffTrackbacks are Off Pingbacks are Off Refbacks are Off Forum Rules

 Similar Threads Thread Thread Starter Forum Replies Last Post yilmazma Electrical 5 12-13-2012 11:58 AM jimcorey Electrical 2 12-08-2012 08:27 AM orobono Electrical 1 10-27-2012 04:25 PM BlueBSH Electrical 11 01-22-2012 09:28 AM cfreak Electrical 31 09-11-2011 09:10 AM

Top of Page | View New Posts