I'm thinking about installing two florescent, surface-mounted lights in my garage on the ceiling. Instead of cutting up the wallboard that is already installed on the ceiling, I was thinking about using the raceway metal channel designed exactly for that use. Both fixtures would tie in to the existing outlet in the ceiling and the two fixtures have a side hole that the wiring would come out of and into the channel. My question is: how do you tie the wiring into the existing outlet in the ceiling when the wiring will be outside of outlet cover (flush to the ceiling)? Do you drill a hole in the wallboard new to the outlet and bring it into the box that way or something else?
There are boxes that mount to the existing outlet and you can run the wiremold out of those. I'll try to find a link in a few minutes.
I would get a box extension like this
and run conduit to the lights.
Since you want to use raceway,
and the raceway would be
Secure it with something like this
Where does the wire feed into the fixtures? back or sides?
Had not thought about lowering the outlet to match the others. Thanks!:thumbsup:
|All times are GMT -5. The time now is 04:19 PM.|
vBulletin Security provided by vBSecurity v2.2.2 (Pro) - vBulletin Mods & Addons Copyright © 2016 DragonByte Technologies Ltd.
User Alert System provided by Advanced User Tagging (Pro) - vBulletin Mods & Addons Copyright © 2016 DragonByte Technologies Ltd.