electric current going to ground ? help
I need some advise, plugged in a industrial sewing machine,
it only has a two wire cord, anyway, it works just fine, and I have
even plugged it is both ways, and the cord Cap has only the small prongs, so you can reverse the Hot / Neu. that didn't change the
problem of a leakage to ground.
when you run one of those proximity testers close to the steel frame, the light blinks and the devices emits the ringing sound.
Which tells you that we have voltage going to ground, the machine
sits on a Cement garage floor, however when I take my Multi - Meter
and I try to test just exactly how much voltage is actually going to
ground, I just get a zero reading. I think that I am doing it correctly,
I put one lead on the frame, and the other lead on to the cement floor. ?
Now, here is what I would like some advise on, how should I ground
this sewing machine, do I just install a three wire power cord, if so
where do I put the green ground wire, to the Frame or the Motor, or maybe both . ? ?
I am also thinking about running a separate ground to all the machines,
as there are four, but the others are A - OK, they have no leakage, but
they are all three wire, do I put in a Ground Rod or Pipe, sink it approximately four foot, ? and run a copper wire to it and the machines,
if so what size, ? anyone that can give me some information it would be appreciated. Thank You PIGEONS
The only way you are going to be able to tell is use a voltmeter and measure from the frame of the machine to a known ground. If you read 0 volts, you have no leakage or short circuit..
the machine is apparently double insulated, or very old. If it is double insulated, it is designed to it will not become a death hazard. If it is simply very old, then yes, a 3 wire cord and attach the ground to the metal parts of the machine. All metal parts should be interconnected within the machine.
The equipment grounding conductor of the cord would connect to the premises egc via the third prong of the plug and recep. You would not need to drive a ground rod for this at the machines.
|All times are GMT -5. The time now is 11:02 PM.|
vBulletin Security provided by vBSecurity v2.2.2 (Pro) - vBulletin Mods & Addons Copyright © 2016 DragonByte Technologies Ltd.
User Alert System provided by Advanced User Tagging (Pro) - vBulletin Mods & Addons Copyright © 2016 DragonByte Technologies Ltd.