Double-pole 3-way switch exist?
I'm installing a 220v 7amp pump and wanted 2 switches. Is there such a thing as a double-pole 3-way switch? All I see are single pole in 3-ways. If not, is it ok to use single-pole 3-way's insteady (heavy duty)???
Sorry, a double pole 3-way switch does not exist. You have two options if you want to be compliant.
1) have a set of regular 3-ways switch a contactor that controls the power to the pump
2) have a set of regular 3-ways switch ONE hot leg of the power to the pump. Using this method, the switch no longer satisfies the "form of disconnect" requirement. You would need to have some form of disconnect at the pump (for when you service it) if you only switch one hot leg with your 3-ways. This may either be a cord and plug arrangement, or an actual double pole disconnect of any variety.
|All times are GMT -5. The time now is 09:01 PM.|
User Alert System provided by Advanced User Tagging (Pro) - vBulletin Mods & Addons Copyright © 2016 DragonByte Technologies Ltd.