jim thanks for your time.
I'm trying to understand what you are suggesting. Is this correct, I need to remove and seperate the wire nut(above the light fixture) and splice the white wire coming from the junction box to the white exiting the light fixture going to the switch? Then splice the black wire returning form the switch to the black wire entering the fixture from the junction box??
Also, the switch claims it can be used as a single pole or a 3way.
I think you have it.
Answers based on the National Electrical Code. Local amendments may apply. Check with your local building officials.